Edited by Dogman, 29 November 2011 - 10:16 PM.
Did you know that you can enjoy many members-only features simply by quickly registering (no CAPTCHA!)?
Registering gives you access to our giveaways, forum features, increased search performance, access to our Download Library, create your own blog & gallery, and more!
Once you have registered, stop by in 'Hello World', and introduce yourself.
HAI, 2 x Yale zwave locks and VRCOP RF+3 integration
Posted 29 November 2011 - 10:05 PM
Posted 30 November 2011 - 10:32 AM
That was very similar to where I was stuck, hyperterminal worked fine, but not the Elk. I used lumenlink and exported the node table to elkrp and everything functioned correctly from the elk, including the lock, which has nothing to do with the lighting table.
Posted 30 November 2011 - 06:25 PM
Posted 01 December 2011 - 06:02 PM
Posted 01 December 2011 - 06:46 PM
Rob: Can you post your text file and rules you are using for getting your lock to work? I finally got my network working again but still no luck on the lock through the M1.
>N2SS98,1,0^M To unlock the door
>N2SS98,1,255^M To lock the door
<n002:000,113,005,022,001 To be received when the door is manually unlocked
I used the back door to open and close the lock (which is on the front door)
WHENEVER Back Door (Zn 3) BECOMES NOT SECURE
THEN SEND THE FOLLOWING TEXT: ">N2SS98,1,0^M" THROUGH PORT 4
WHENEVER Back Door (Zn 3) BECOMES SECURE
THEN SEND THE FOLLOWING TEXT: ">N2SS98,1,255^M" THROUGH PORT 4
WHENEVER THE FOLLOWING TEXT IS RECEIVED: "<N002:000,113,005,022,001" THROUGH PORT 4
THEN SEND EMAIL MESSAGE 1 TO [email protected] (Email1)
Hope that helps, the send messages work reliable, but I can't get the receive rule to work at all, and I have tried a variety of texts.....
Posted 03 December 2011 - 12:39 PM
Posted 03 December 2011 - 03:38 PM
Posted 03 December 2011 - 06:09 PM
But I'm pretty sure that I see a carriage return in Hyperterminal (otherwise everything received would be on one line).
I emailed Brad about the new z-wave interface, and he didn't have an update.
Posted 03 December 2011 - 06:11 PM
Posted 03 December 2011 - 11:36 PM
Well I don't get that part cause none of my controllers were recognized using the 184.108.40.206 software and I was unable to associate anything to them. Go figure. The Leviton rep said their Vizia RF installer developers were aware of issues on that version but my problem was a new one to them. So I cannot get responses either when testing for a manual lock or unlock. Looking at the Text string box in ELK RP it says that all received text strings must have a Carriage return and since the VRCOP+3 doesn't seem to do that on responses maybe this is why we can't get it to work. I am assuming the M1SXP doesn't send anything to the M1 unless it sees that carriage return. In looking at the manual for the M1XSP they mention it as well but not related to the Vizia stuff but related to UPLINK 2500 so it must send a carriage return when it communicates. I am thinking this might be why ELK is releasing a new special Z-wave interface device any day now. I also went back to one of my old posts and remember I emailed ELK about this months ago when the VRCOP3 came out (before I bought one) and they said it will control the locks but will not be able to get status feedback from them. I totally forgot about this part until I was just digging through some email. The new device was supposed to be released 4th quarter this year but I don't see anything on their website about it. So sounds like if we want status updates on locks we get to give ELK more $.
dogman, what type of controllers were you trying to associate? I can't get the stick to identify either an ha07 or a ge 45600 remotes...
Posted 03 December 2011 - 11:45 PM
Posted 22 December 2011 - 07:08 PM
Posted 22 December 2011 - 07:12 PM
Posted 22 December 2011 - 10:55 PM
0 user(s) are reading this topic
0 members, 0 guests, 0 anonymous users