Did you know that you can enjoy many members-only features simply by quickly registering (no CAPTCHA!)?
Registering gives you access to our giveaways, forum features, increased search performance, access to our Download Library, create your own blog & gallery, and more!
Once you have registered, stop by in 'Hello World', and introduce yourself.
PIM no signal (SPIM-01 UPB GEN II)
Posted 29 December 2011 - 03:22 PM
OK, today i replaced phase coupler, because i thought previous was broken, and nothing is changed. Still able to control half of my dimmers from one receptacle and the rest of them from another. So i thinking to buy SA phase coupler with phase inversion. This is my last hope
And i still can't get feedback from dimmers in PCAccess. Everything seems work fine with Haiku, i can control light level, change scenes and see status of those dimmers but this is only with iPad or PC...
Posted 29 December 2011 - 05:50 PM
What kind of "Status update" are you trying to get in PCAccess?
Posted 29 December 2011 - 07:58 PM
Posted 29 December 2011 - 08:51 PM
When You have PCAccess connected and On-Line to the Omni and you look at the status page (tab4), is it different than Haiku?
That sounds awfully unlikely if Haiku is showing the correct status.
Posted 29 December 2011 - 09:27 PM
Posted 29 December 2011 - 11:05 PM
Everything seems work fine with Haiku, i can control light level, change scenes and see status of those dimmers but this is only with iPad or PC...
Looking at your file again.
Did you enter the correct UPB network password? I assume yes since you say you can control things.
Do you have a second PIM so you can monitor the UPB traffic with UPStart?
If yes, then hook up the PIM to a PC, run UPStart and open the log viewer.
Do you see the Omni sending the status request messages?
Are the units responding to the status requests?
Posted 29 December 2011 - 11:30 PM
Posted 30 December 2011 - 01:35 AM
AFAIK the UPB message protocol didn't change between Gen I and II. I run a mixture.
Without seeing the UPB traffic I don't know what else to tell you.
I wonder if you might have a bad serial cable between the PIM and Omni.
Maybe the transmit line is connected but the recieve line isn't.
Posted 30 December 2011 - 08:39 AM
BTW in another upb network old pcs pim work without disconnections.
Posted 30 December 2011 - 08:43 AM
Posted 06 January 2012 - 10:46 PM
Problem was with cable that connects PIM to Omni board. This cable came with HAI PIM... Now i see dimmers status changes almost immediately
Jeff, one more time thank you for your hint to check cable.
0 user(s) are reading this topic
0 members, 0 guests, 0 anonymous users