I have established installing some UPB switches in my house. I am now attempting to replace a legacy 3way with some Simply Automated USR-40A and US1-40.
The wiring diagrams I see for these switches does not conform to how I am seeing things wired up that I am trying to replace.
in one gang box is a lutron ctcl-153p this box has line power in and a connection to the remote wall switch. (black/red/tagged white) the remote wall gang box has a three way toggle switch . red and black on one side, tagged white going into it.
I am looking at the Simply Automated user guides and it looks like Line and Neutral are in both gang boxes for USR-40A and US1-40?
This circuit has just this light on it. no other lights or loads. maybe the user guide implies the switches can be in series for other loads? or is it to two different circuit breakers?
appreciate any help in replacing these switches.