Guess I answered my own question from the board diagram in the installation manual.
1. SWITCH 12V, AUXILIARY 12V, CONSOLE, AND OUTPUTS 1-8 ARE INCLUDED IN THE TOTAL DEVICE LOAD, WHICH CANNOT EXCEED 1 AMP.
IN UL INSTALLATIONS, THE TOTAL DEVICE LOAD CANNOT EXCEED 250mA.
2. SOUNDERS CANNOT EXCEED 1 AMP, SPLIT BETWEEN INTERIOR AND EXTERIOR HORN OUTPUTS. IN UL INSTALLATIONS, SOUNDERS CANNOT EXCEED 350mA.
Outputs 1 - 8 can supply a maximum of 100 mA each. These outputs are included in the total DEVICES load, which cannot
exceed 1A. If the Interior or Exterior Sounder is configured to an Output Type, the HORN outputs can supply a maximum of
1A. HORN outputs are included in the total HORNS load, which can not exceed 1A.
I'll have a packed panel and have the feeling that all consoles, motion detectors, smoke detectors, sounders and strobes should be powered externally. That should leave plenty for combustible gas detectors, Sure Action processors, waterbugs, expansion boards, etc, etc. I'll have to run the numbers.
Edited by kwschumm, 09 April 2018 - 07:23 PM.